Alarm Alert VM500
8 Channel, User Voice Callout Alarm Dialer
The Automatic Alarm Autodialer shall be microprocessor based
and fully user programmable.
accept up to eight (8) dry contact or 24 volt logic inputs from field devices
in the –LV
model variation or eight (8) high voltage inputs in the –HV variation. Battery
backup shall be standard.
Inputs shall be programmable for their status and may be
normally open or normally closed in the non-alarm condition.
The autodialer shall continuously monitor its
power supply and dial out in the case of a power failure.
All inputs shall have programmable time
delays to avoid false alarms.
The dialer shall be capable of calling up to four (4) user
programmed call-out phone numbers, pagers or answering machines.
Local station identification messages and unique channel
alarm messages shall be user recordable and up to five seconds long.
Once an alarm condition exists the dialer
shall call the first number in sequence and deliver the alarm condition
The user shall have the ability
to stop any further call out notifications by entering a four (4) digit PIN
If the PIN is not entered, the
dialer shall continue to call out to the other programmed numbers.
The dialer shall be programmable to deliver
reminder calls after a selectable interval.
An integral relay shall be standard and shall be
programmable for remote control or local activation upon any alarm condition.
The autodialer should be capable of receiving query calls
from the user and reciting the status of all alarm conditions on demand.
- Enclosure: flame
retardant ABS plastic 94-5VA
- Size: 8.79 x 4.62 x
2.25, weight 27 lbs.
- Temperature Limits:
32º F to 125º F
The Automatic Alarm Dialer shall be Sigma Controls’ Alarm